The primary consideration when working on outdoor wiring is to provide both mechanical protection (to prevent damaging the electrical installation and to protect you from accidental contact with live circuits), and to protect the installation from the elements, like rain, snow, and ice.
As with any electrical project, every precaution should be taken to protect yourself and others from electrical shock; the most important precaution being to never work on live circuits. Ensure that the power is off before working on any electrical circuit!
Refer to our safety fundamentals page on our website, and any other useful safe work practices resource at your disposal. Any and all outdoor wiring codes must be followed, permits obtained, and inspections performed as required.
There are two main categories that outdoor wiring installations could be classified as:
To provide a safe amount of light to traffic areas such as stairwells, steps, sidewalks, gates, outdoor cooking facilities, etc.
To illuminate and accent plants, trees, or shrubs, architectural features, artwork or pools and spas. Decorative lighting can also be functional.
Cable and Conduit for Outdoor Wiring
For outdoor and underground wiring, you can use cable suitable for exposure to the elements such as NMWU-90, or direct burial cable of the appropriate rating, conduit (both metal, plastic, or liquid-tite flexible conduit) and wire, or a combination of both. It is important to check both national and local code rules for outdoor wiring installation requirements.
Ground Fault Circuit Protection for Outdoor Wiring
Ground fault circuit protection is required for most outdoor electrical circuits so again, check with the local electrical authority for the requirements for your particular outdoor wiring project.
All outdoor electrical fittings and device boxes must be rated for outdoor use, installed with supplied gaskets and appropriate entrance fittings.
Switches used outdoors must be protected with weatherproof covers and gaskets to prevent exposure to the elements.
Outdoor Light Fixtures
All light fixtures installed outdoors must be rated for, and approved for outdoor installation, and all gaskets provided must be installed and maintained in good condition. Make sure that the bulbs are rated for outdoor use as well.
All receptacles and outlets must be rated for outdoor use and be fitted with the correct weatherproof cover plate and gaskets. Check your local jurisdiction for the specific requirements for weatherproof cover plates for receptacles.
The National Electrical Code mandates that all outdoor receptacles be fitted with an in use cover plate. These devices provide protection for the outlet even when a cord is plugged into the outlet and are available in many styles. Not all areas have adopted all of, or even parts of the N.E.C., so again, i...